Actual product may vary based on spec selection.
Threaded Post Camlock Connection Box 400A 347/600V -Female Neutral
The Cam Lock Connection Box acts as a connection point or junction box in between your generator and your load, similar to that of our Generator Docking Station. The color-coded CAM Lock connections match typical portable generator standards. The CCB can be used to connect to switchgear or switchboards without having to call an electrician every time you need to connect your generator to the load. Simply connect your cables to the CCB from the generator to provide reliable temporary power to commercial buildings or other temporary power connections.
The Cam Lock Connection Box comes equipped with industry standard Series 16 CAM Connectors. The Cam Connectors are UL/CSA Listed single-pole and they are color coded to phase-match appropriate voltages. The Phase and Ground Cams are available in Male or Female. The box can be configured with bottom 90° straight camlocks, right 90° straight camlocks, or right 45° angled camlocks layouts. 90° Cam Lock connectors are compatible with either clear snapback covers or caps and lanyards, while our 45° Cam Lock connectors are only compatible with caps and lanyards.
The Cam Lock Connection Box can stand up to residential, commercial, and industrial working conditions. This enclosure is NEMA 3R, IEC 60529, and IP 66 rated with a foam gasket and recessed hinge so it can perform indoors or outdoors withstanding against exposure to dirt, debris, and wind driven rain. The Cam Lock Connection box is built from durable 0.075” (14-gauge) carbon steel to ensure a long life and corrosion resistance.
Camlock Connection Box is covered by a manufacturer’s warranty for a period of one (1) year from date of shipment from the manufacturer.
- Wall Mount
- Threaded Post
- Maximum Amperage 400A
- Maximum Voltage Rating up to 600V
- Box Uses 347/600VAC
- Red/Blk/Blu/Wht/Grn Color Configuration
- 20” H x 20” W x 8” D
- Female Neutral Connector
- Industry Standard Series 16 CAM Lock Connectors
- Assembled with All UL-Listed Materials
- Phase & Ground Cam Choice of Male or Female
- Bottom 90°, Right 90°, or Right 45° Layout
- 90° comes with Clear Snapback Covers or Caps and Lanyards
- 45° comes with Caps and Lanyards
- NEMA 3R Rated
- Enclosure IEC 60529 & IP 66 rated
- 0.075” (14-Gauge) Carbon Steel
- Generator Connections
- Load Bank Testing Connections
- Switchgear Connections
- Portable Power
- Temporary Power
Please Note: Power Assemblies products are built to order. Please check lead time under the specification tab to avoid any delays. Items will ship by your selected shipping method upon completion. Customers have the option to add an expedited fee of 25% if needed before the lead time period. This fee will not be charged online as we need prior confirmation from the production facility.